We are using DM water in process. The DM water rinse stores in 60 KL tank.
after some time we get off smell in water, which is not in fresh DM water?
Gopichand Mahajan - Aurangabad ^
It may be an odor due to amines that are coming from the anion resin. This is common on new anion resins, and on resins that have been idle for a long time and then put into service. It is most commonly associated with Strong Base Type I resins with trimethyl amine functional groups.
Lyle Kirman consultant - Cleveland Heights, Ohio ^
finishing.com is made possible by ... this text gets replaced with bannerText
Disclaimer: It's not possible to fully diagnose a finishing problem or the hazards of an operation via these pages. All information presented is for general reference and does not represent a professional opinion nor the policy of an author's employer. The internet is largely anonymous & unvetted; some names may be fictitious and some recommendations might be harmful.
If you are seeking a product or service related to metal finishing, please check these Directories: