The finishing.com Hotline: Serious Education ... plus the most fun you can have in metal finishing. Ted Mooney, Webmaster
Use of Ferric Sulfate as a coagulant for water treatment
We are dealing in the Processing of Sports Socks. We are at the moment in a phase of erection/commissioning of Effluent treatment plant to treat the Waste Water of our Dye-House. I have some technical questions.
1- What is the main difference between Ferric Sulfate and Ferrous Sulfate to be used as a Coagulant for the plant.
2- Is there possibility that Ferric sulfate after working as a coagulant will further increase the TDS of the treated water?
3- How Ferric Sulfate will chemically interfere the process of the effluent treatment to be act as a coagulant?Ijaz Hussain
manager processing - Faisalabad, Punjab, Pakistan
You haven't given enough information on the effluent composition, treatment processes and efficacy, and effluent limits. In any event, some jar testing‹ should be done. 1) Ferric sulfate is superior as a coagulant, especially for co-precipitating other metals as hydroxides. "Not only do the Fe(III) cations as the positively charged basic salt ions neutralize the negative charge on finely dispersed precipitates, they also (in slight excess) act as flocculating agents. In consequence, readily sedimentable and easily filterable materials are formed". L. Hartinger, p. 194 in "Handbook of Effluent Treatment & Recycling for the Metal Finishing Industry" [link is to product info at Amazon]
However, if your treated effluent contains residual excess oxidizer or Cr(VI), Fe(II) may be advantageous as a reducing agent. Also, Fe(III) compounds are more expensive than Fe(II), and their solutions are less easily pumped due to lower solubilities. It may be preferable to use Fe(II) and then convert it to Fe(III) by air agitation or via reaction with excess oxidizer as mentioned or with hydrogen peroxide.
2) Yes, either Fe sulfate will increase the TDS, as the Fe precipitates as hydroxide, leaving sulfate ion in solution. Soluble sulfate can be lowered to ~2000 ppm with lime, but this may be too high for effluent limits, e.g., for reuse in irrigation. You can add iron using ferric chloride, but chloride is also difficult to remove (except by energy intensive processes such as reverse osmosis). You can also add iron ions without the undesirable anions by passage through scrap iron or an electrocoagulation unit with mild steel plates.
3) Add the coagulant after chemical treatment (and before final pH adjust and polymer addition); it should not interfere with the treatment. It should improve flocculation and settling.Ken Vlach
- Goleta, California
finishing.com honored Ken for his countless helpful|
& well researched responses. He 'disappeared' in
2008, never answering our several inquiries about
his situation. But we believe that this is his obit
and would greatly appreciate hearing from anyone
who knew him. Thank you Ken, and rest in peace.
February 3, 2010
I am looking for Reference Water Treatment Plants using Ferrous Sulfate as coagulant we could contact ?Alex Moubarak
February , 2010
Hi, Alex. I think the best way forward would be contact a major supplier of ferrous sulfate and ask them for the names of a few of their water treatment customers. Alternately a literature search for technical articles on the subject should get you there. Good luck.
Ted Mooney, P.E. RET
Pine Beach, New Jersey